Herborner Pumpenfabrik - Emax
The company had in the year 2007 a peak load of 600 kW. They had been charged with the three peak loads of the three highest month measurements.
The maximum load could be reduced by 180 kW down to 420 kW. This reduction has been achieved by means of a PDMS, i.e. through short term disconnection and speed reduction of pre-defined loads.
Typical loads were VFD driven ventilators, which could be reduced in speed, as well as large scale compressors. As a first step a AMR (automatic meter reading) system for the various media, such as Gas, Water, Oil, Electricity had been installed. These data are used for some tax benefit reasons.
On top a level monitoring system for oxygen and glass sand has been implemented. In case of undercutting the minimum level an Email is triggered informing the purchasing department ordering new materials.
|Project name:||HP Peak Demand Management|
|Market segment:||Industry, pump manufacturer|
|Type of application:||Peak demand management (PDMS) and cost center management|
Type / Quantity of Measurement Devices
|UMG 507||# 52.15.222||1 Device|
|UMG 604E||# 52.16.002||1 Devices|
|UMG 96S||# 52.13.001||5 Devices|
|Prodata||# 52.11.001||2 Devices|
|Ethernet||UMG604E, 507 (Emax)|
|Modbus, RS485||Between UMG604E and the UMG96S / Prodata|
|GridVis and UMG604E Homepage||Configuration, graphical interface, reporting, alarm management .|
|Energy Saving||17 Euro /kW (17€ x 180kW x 12=36.720€ p.a.)|
|Transparency||Easier negotiation with power utilities|
|Quick failure analysis||Reduction of maintenance cos|
|Benchmarking||Comparison of the various production lines|
|Reduction of peak demand||Stabilizing of the energy supply|